BLOWN-IN INSULATION - CONTENTS: How much does blown-in building insulation settle?
Does blown-in insulation need a vapor barrier? Identifying & inspecting cellulose building insulation. Properties and R-values of different building insulation products. Description of Non-asbestos materials sometimes mistaken for asbestos in buildings
Blown-in Building Insulation: settlement, vapor barriers, condensation, R-values, voids
This document assists building buyers, owners or inspectors who need to diagnose, identify, or improve building insulation for new construction or retrofit and energy savings projects.
The question-and-answer article below paraphrases, quotes-from, updates, and comments an original article from Solar Age Magazine and written by Steven Bliss.
Various materials have been used as poured-in or blown-in building insulation but the two most common are cellulose insulation illustrated in our photo and chopped fiberglass insulation illustrated in our next photo (below).
Blown In Building Insulation Characteristics, Advice, Moisture or Condensation Concerns
Does blown-in insulation settle and need to be added as time goes by?
Our house doesn't seem as warm as it did at first, though it could be because we are getting old. There is no vapor barrier - the builder said that I didn't need a vapor barrier in this climate. - Carl Whitis, Belen NM
Above: chopped pink fiberglass insulation poured or blown into an attic in a somewhat sloppy uneven installation. This chopped fiberglass insulating material is discussed at FIBERGLASS INSULATION IDENTIFICATION.
Settlement in Blown in Building Wall Insulation
If the building insulation was blown in at the proper density, it shouldn't settle. This is true for both blown-in fiberglass and blown-in cellulose insulation. (Typically we're talking about insulation blown into building wall cavities)
If blown-in insulation has settled however, the gap at the top of the wall may sharply reduce the R-value of the wall.
Assume R-11 blown-in insulation in a wall cavity settles enough to create a void equal to 10 percent of the wall area.
This would drop the effective R-value of the wall from R-13 to R-9.75 - a 25-percent reduction in insulating value and a 25 percent increase in heat loss through the wall.
You can determine whether or not blown-in wall insulation has settled by a thermograph scan of the building.
Our photo (above left) shows an inspection test cut to expose blown-in cellulose in a building wall. - DF
Other Voids in Blown-in Building Wall or Ceiling Insulation
Watch out: in some blown-in building insulation retrofit projects we have occasionally found significant insulation voids where the installer was careless, or where the installer did not anticipate blockages in the wall cavity formed by diagonal bracing [Image file] or fire blocking.
An infra-red or thermal scan of a heated building during cold weather will make such insulation voids obvious - DF.
[We did indeed observe significant shrinkage, not settlement, in UFFI blown-in insulation in some homes insulated with that product in the 1970's, particularly if the product was not properly mixed in the first place.
Voids in UFFI Foam Insulation Pumped Into Building Cavities
Popular in the U.S. during the Arab Oil Embargo Urea Formaldehyde Foam Insulation was used as a pumped-in insulation retrofit in previously-un-insulated building walls and ceilings, particularly in the northeastern U.S. states and in some areas of Canada. Depending on how the product was mixed and installed, significant shrinkage occurred as the insulation dried and cured, leaving air bypass leaks around the sides and tops of these blocks of foam in building walls and around all sides of UFFI in building ceilings.
Why Does our Blown-in Insulated House Now Feel Colder?
Your house may feel cold because the lack of a vapor barrier has let moist air from the house interior (or leaks in the house interior walls) has let moisture enter the walls.
As moisture enters building walls, it cools, causing condensation in the wall cavity. The effect is similar to an actual leak into the building wall but perhaps less severe, and possibly not a problem.
Effects of Moisture in Building Wall Cavities - Do We Need a Vapor Barrier?
If we have a limited amount of moisture in the wall cavity:
moisture will be absorbed into the wall framing and insulation
moisture will then diffuse or convect to the outside air or
moisture will return to the house itself as the indoor relative humidity level drops
Even limited moisture leaking into some building walls can accumulate, leading to mold or other building problems depending on the wall structure and materials. For example leaks into EIFS synthetic stucco walls have led to serious rot and mold problems on some buildings.
If insulation actually gets wet (from accumulated condensation or from a leak into the wall cavity or ceiling cavity) the insulation becomes less effective, and you may feel the result as a "colder house" or in some unfortunate cases, as a "moldy house" with indoor air quality problems depending on the amount of moldy air moving in and out of building cavities.
If moisture returns to the building interior or exterior (cases 2 and 3 above) then no harm may have been done.
Watch out: building insulation that has been wet from leaks or accumulated moisture may invite mold growth, insect attack, and rot, all of which can eventually lead to the need for costly repairs.
Studies of several hundred houses without vapor barriers in Spokane WA and Portland OR, performed in the 1980's by George Tsongas of Portland State University found no structural damage to the buildings and only occasional higher than average moisture levels in the building framing or insulation.
Albuquerque NM (your location) is dryer than Spokane and has fewer degree days, so you should not have in-wall humidity problems unless they originated in building leaks.
Here we include solar energy, solar heating, solar hot water, and related building energy efficiency improvement articles reprinted/adapted/excerpted with permission from Solar Age Magazine - editor Steven Bliss.
"Spray-applied cellulose insulation, which is most often used in new construction, is damp-sprayed, not wet - an important distinction. In the old days, [cellulose insulation] was a wet-applied product, and you could squeeze liquid moisture out of it.
For quite some time now, only a very small amount of moisture is added to damp-sprayed cellulose, definitely not enough to be able to squeeze water out of it. Under normal conditions, the cellulose insulation is ready to be covered by drywall in 24 hours, far less than the time that is routinely scheduled between the insulation and drywall jobs [in new construction]."
"In addition, cellulose manages moisture." According to Fallow [we are not sure we agree], "Cellulose insulation requires no vapor barrier in the overwhelming majority of installations. It does an excellent job of limiting air movement, and because it is hygroscopic [definition: hygroscopic means a substance tends to absorb moisture from air], it manages moisture as well.
Some insulations require vapor barriers because they do such a poor job of preventing air movement, air that can carry moisture with it.
The problem is that ... moisture and air don't always move in the same direction thorough a building, depending on the time of year. So what about those products that need a vapor barrier? Effectively half the year it's on the wrong side of the wall. Cellulose [that is blown in without a vapor barrier] doesn't have that problem."
Watch out: In our opinion the views above need some clarification:
It is accurate that building wall cavity insulation can safely "absorb" moisture driven into the wall cavity, store it, and later release it back to the living area as seasons and air and moisture movement direction change. We discuss the safe movement of moisture in and out of building cavities at MOISTURE in BUILDING WALLS, EFFECTS.
It can also the case that if moisture driven into a wall (usually most severely at wall penetrations such as openings at receptacles or light fixtures) is excessive in amount (such as in a poorly vented bathroom or in a home with water entry troubles) the amount can be enough to saturate the insulation (mold and loss of R-value). The ability of different building insulation materials to absorb moisture vapor and later return it safely to the building interior varies by insulation product.
Also, depending on the wall or ceiling's total R-value, moisture can pass through the insulation to the exterior sheathing where it condenses back to liquid form. That's a problem that invites mold growth, structural rot, and insect attack.
Fallow's explanation above may confuse some readers who mix up the need for a vapor barrier (keeping moisture out of a wall) and the need for an air barrier (keeping wind effects out of a wall from outside and/or minimizing air movement in and out of a wall from inside the building). Exterior house wrap is specifically intended to be an air barrier, not a moisture barrier, so that if moisture does pass through a wall's insulation it can continue to pass to the outdoors.
Or more generally, we place a vapor barrier on the "warm side" of a wall (or ceiling or floor) in order to prevent moisture from moving into and accumulating in the building cavity. In northern climates invariably that means the vapor barrier goes inside the building. In some southern climates where air conditioning is used, the "warm" side of the wall is actually the building exterior and a vapor barrier may be placed there rather than indoors.
A Few Other Warnings about Blown-In Building Insulation
Watch out: don't blow ceiling insulation into or around electrical fixtures or wiring that can create an overheating or fire hazard. Examples of problems to avoid when blowing insulation into a building include [-DF]
Blocking or covering up attic or under-roof ventilation can lead to a building moisture problem where there was none before.
Our photo (left) shows a building ridge-vent that was jammed full of blown-in cellulose insulation during an insulation retrofit job in upstate New York.
The result was a blocked under-roof or attic ventilation exit pathway, moisture accumulation, and a mold problem bad enough that the insulation and ceiling had to be removed and the attic area cleaned.
Blocking or covering-up knob-and-tube electrical wiring. This type of electrical wiring was intended to be hung in open air.
If it is covered by insulation, depending on circuit usage it may overheat, damaging its insulation, becoming unsafe, perhaps a fire hazard.
Blocking or covering up pot lights (recessed ceiling lights) that are not rated to be covered by insulation can lead to overheating and a fire.
The link to the original Q&A article in PDF form immediately below is preceded by an expanded/updated online version of this article.
Q&A on Blown-in Insulation - PDF version, use your browser's back button to return to this page
Continue reading at CELLULOSE LOOSE FILL INSULATION or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Questions & answers or comments about -.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Steve Bliss's Building Advisor at buildingadvisor.com helps homeowners & contractors plan & complete successful building & remodeling projects: buying land, site work, building design, cost estimating, materials & components, & project management through complete construction. Email: email@example.com
Steven Bliss served as editorial director and co-publisher of The Journal of Light Construction for 16 years and previously as building technology editor for Progressive Builder and Solar Age magazines. He worked in the building trades as a carpenter and design/build contractor for more than ten years and holds a masters degree from the Harvard Graduate School of Education.
Excerpts from his recent book, Best Practices Guide to Residential Construction, Wiley (November 18, 2005) ISBN-10: 0471648361, ISBN-13: 978-0471648369, appear throughout this website, with permission and courtesy of Wiley & Sons. Best Practices Guide is available from the publisher, J. Wiley & Sons, and also at Amazon.com
Asbestos products and their history and use in various building materials such as asphalt and vinyl flooring includes discussion which draws on ASBESTOS, ITS INDUSTRIAL APPLICATIONS, ROSATO 1959, D.V. Rosato, engineering consultant, Newton, MA, Reinhold Publishing, 1959 Library of Congress Catalog Card No.: 59-12535 (out of print).
Asbestos Identification and Testing References
Asbestos Identification, Walter C.McCrone, McCrone Research Institute, Chicago, IL.1987 ISBN 0-904962-11-3. Dr. McCrone literally "wrote the book" on asbestos identification procedures which formed
the basis for current work by asbestos identification laboratories.
Stanton, .F., et al., National Bureau of Standards Special Publication 506: 143-151
Pott, F., Staub-Reinhalf Luft 38, 486-490 (1978) cited by McCrone
ASHRAE resources on building insulation, dew point and wall condensation - see the ASHRAE Fundamentals Handbook, available in many libraries. The following three ASHRAE Handbooks are also available at the InspectAPedia bookstore in the third page of our Insulate-Ventilate section:
2005 ASHRAE Handbook : Fundamentals: Inch-Pound Edition (2005 ASHRAE HANDBOOK : Fundamentals : I-P Edition) (Hardcover), Thomas H. Kuehn (Contributor), R. J. Couvillion (Contributor), John W. Coleman (Contributor), Narasipur Suryanarayana (Contributor), Zahid Ayub (Contributor), Robert Parsons (Author), ISBN-10: 1931862702 or ISBN-13: 978-1931862707
2004 ASHRAE Handbook : Heating, Ventilating, and Air-Conditioning: Systems and Equipment : Inch-Pound Edition (2004 ASHRAE Handbook : HVAC Systems and Equipment : I-P Edition) (Hardcover)
by American Society of Heating, ISBN-10: 1931862478 or ISBN-13: 978-1931862479
"2004 ASHRAE Handbook - HVAC Systems and Equipment The 2004 ASHRAE HandbookHVAC Systems and Equipment discusses various common systems and the equipment (components or assemblies) that comprise them, and describes features and differences. This information helps system designers and operators in selecting and using equipment. Major sections include Air-Conditioning and Heating Systems (chapters on system analysis and selection, air distribution, in-room terminal systems, centralized and decentralized systems, heat pumps, panel heating and cooling, cogeneration and engine-driven systems, heat recovery, steam and hydronic systems, district systems, small forced-air systems, infrared radiant heating, and water heating); Air-Handling Equipment (chapters on duct construction, air distribution, fans, coils, evaporative air-coolers, humidifiers, mechanical and desiccant dehumidification, air cleaners, industrial gas cleaning and air pollution control); Heating Equipment (chapters on automatic fu
el-burning equipment, boilers, furnaces, in-space heaters, chimneys and flue vent systems, unit heaters, makeup air units, radiators, and solar equipment); General Components (chapters on compressors, condensers, cooling towers, liquid coolers, liquid-chilling systems, centrifugal pumps, motors and drives, pipes and fittings, valves, heat exchangers, and energy recovery equipment); and Unitary Equipment (chapters on air conditioners and heat pumps, room air conditioners and packaged terminal equipment, and a new chapter on mechanical dehumidifiers and heat pipes)."
1996 Ashrae Handbook Heating, Ventilating, and Air-Conditioning Systems and Equipment: Inch-Pound Edition (Hardcover), ISBN-10: 1883413346 or ISBN-13: 978-1883413347 ,
"The 1996 HVAC Systems and Equipment Handbook is the result of ASHRAE's continuing effort to update, expand and reorganize the Handbook Series. Over a third of the book has been revised and augmented with new chapters on hydronic heating and cooling systems design; fans; unit ventilator; unit heaters; and makeup air units. Extensive changes have been added to chapters on panel heating and cooling; cogeneration systems and engine and turbine drives; applied heat pump and heat recovery systems; humidifiers; desiccant dehumidification and pressure drying equipment, air-heating coils; chimney, gas vent, fireplace systems; cooling towers; centrifugal pumps; and air-to-air energy recovery. Separate I-P and SI editions."
Construction Waterproofing Handbook, Michael T. Kubal. Quoting:
... an all-inclusive, project-simplifying guide for waterproofing and construction professionals. This comprehensive answer-packed resource is loaded with the up-to-date, clearly-defined information you need on every project, including work on the building envelope, below-grade, above-grade, and remedial waterproofing.
Brick Nogging, Historical Investigation and Contemporary Repair, Construction Specifier, April 2006. Historical use of brick in timber-framed buildings, drawing on the investigations of the Kent Tavern in Calais, VT.
"Brick nogging is a European method of construction which was brought to the new world in the early-nineteenth century. It was a common construction method that employed masonry as infill between the vertical uprights of wood framing." -- quoting the web article review.
"Energy Savers: Whole-House Supply Ventilation Systems [copy on file as /interiors/Energy_Savers_Whole-House_Supply_Vent.pdf ] - ", U.S. Department of Energy energysavers.gov/your_home/insulation_airsealing/index.cfm/mytopic=11880?print
"Energy Savers: Whole-House Exhaust Ventilation Systems [copy on file as /interiors/Energy_Savers_Whole-House_Exhaust.pdf ] - ", U.S. Department of Energy energysavers.gov/your_home/insulation_airsealing/index.cfm/mytopic=11870
"Energy Savers: Ventilation [copy on file as /interiors/Energy_Savers_Ventilation.pdf ] - ", U.S. Department of Energy
"Energy Savers: Natural Ventilation [copy on file as /interiors/Energy_Savers_Natural_Ventilation.pdf ] - ", U.S. Department of Energy
"Energy Savers: Energy Recovery Ventilation Systems [copy on file as /interiors/Energy_Savers_Energy_Recovery_Venting.pdf ] - ", U.S. Department of Energy energysavers.gov/your_home/insulation_airsealing/index.cfm/mytopic=11900
"Energy Savers: Detecting Air Leaks [copy on file as /interiors/Energy_Savers_Detect_Air_Leaks.pdf ] - ", U.S. Department of Energy
"Energy Savers: Air Sealing [copy on file as /interiors/Energy_Savers_Air_Sealing_1.pdf ] - ", U.S. Department of Energy
Fiberglass: Indoor Air Quality Investigations: Health Concerns About Airborne Fiberglass: Fiberglass in Indoor Air from HVAC ducts, and Building Insulation
Insulate & Weatherize (Taunton's Build Like a Pro), Bruce Harley. Review quoted:
An engineer who trains builders in energy-efficient construction, Harley offers a wealth of information that will allow readers to improve their home's efficiency, saving both money and natural resources. After an introductory section that explains the underlying principles of heat transfer, insulation, and air quality, Harley demonstrates basics such as weather-stripping and moves forward through advanced projects including insulation and major upgrades. Short "Pro Tips" as well as sections labeled "Trade Secrets," "What Can Go Wrong," and "In Detail" provide a great deal of helpful information. Increasing energy efficiency is one of the easiest ways for homeowners to save money
Insulation Types, table of common building insulation properties from U.S. DOE. Readers should see INSULATION R-VALUES & PROPERTIES our own table of insulation properties that includes links to articles describing each insulation material in more detail.
The National Institute of Standards and Technology, NIST (nee National Bureau of Standards NBS) is a US government agency - see www.nist.gov
"A Parametric Study of Wall Moisture Contents Using a Revised Variable Indoor Relative Humidity Version of the "Moist" Transient Heat and Moisture Transfer Model [copy on file as/interiors/MOIST_Model_NIST_b95074.pdf ] - ", George Tsongas, Doug Burch, Carolyn Roos, Malcom Cunningham; this paper describes software and the prediction of wall moisture contents. - PDF Document from NIS
Piquet Wall Construction: See this photo of
piquet wall construction - involving timber-framed wall construction with long top girts, diagonal timber bracing, and small diameter logs
placed vertically along with concrete chinking to fill in the wall plane.
Plank House Construction: weblog from plankhouse.wordpress.com/2009/01/25/plank-house-construction/ and where plank houses were built by native Americans, see
Large 1:6 Scale Plank House Construction / P8094228,
Photographer: Mike Meuser
06/12/2007 documented at yurokplankhouse.com where scale model Museum quality Yurok Plank Houses are being sold to raise money for the Blue Creek - Ah Pah Traditional Yurok Village project.
Principles of Heating, Ventilating, And Air Conditioning: A textbook with Design Data Based on 2005 ASHRAE Handbook - Fundamentals, Harry J., Jr. Sauer, Ronald H. Howell, William J. Coad. Quoting
... textbook for college level HVAC courses or independent study and review, especially when combined with the 1997 ASHRAE Fundamentals Handbook. Contains the most current ASHRAE procedures and definitive, yet easy to understand, treatment of building HVAC systems -- from basic principles through design and operation. Dual units of measurement.
Re-Bath, tub lining products is a bath tub relining manufacturer and distributor located in Tempe, Arizona - see rebath.com
Rubblestone Wall Filler: See this Lartigue House using exterior-exposed rubblestone filler between vertical timbers of a post and beam-framed Canadian building.
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones