Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ACOUSTICAL SEALANT CHOICES
AIR BYPASS LEAKS
AIR LEAK SEALING PROCEDURE
AIR TEST FOR MOLD: ACCURACY
ALLERGEN TESTS for buildings
ALLERGENS in BUILDINGS, RECOGNIZING
ANIMAL ALLERGENS / PET DANDER
ANIMAL ENTRY POINTS in buildings
APPLIANCE EFFICIENCY RATINGS
BLOWER DOORS & AIR INFILTRATION
BLOWER FAN CONTINUOUS OPERATION
BLOWER FAN OPERATION & TESTING
BUCKLED FOUNDATIONS due to INSULATION?
BUILDING NOISE DIAGNOSIS & CURE
CARPET PADDING ASBESTOS, MOLD, ODORS
CARPETING, SELECTION & INSTALLATION
CATHEDRAL CEILING VENTILATION
CHIMNEY INSPECTION DIAGNOSIS & REPAIR
COMBUSTION AIR for TIGHT buildings
DIRECTORY of MOLD / ENVIRONMENTAL EXPERTS
ENGINEERED WOOD Flooring
FIREPLACES & HEARTHS
FLOOR TYPES & DEFECTS
FRAMING DETAILS for BETTER INSULATION
FREEZE-PROOF A BUILDING
FROST HEAVES, FOUNDATION, SLAB
HEAT LOSS in BUILDINGS
HOUSE DOCTOR, how-to be
INDOOR AIR QUALITY IMPROVEMENT GUIDE
Insulation Air & Heat Leaks
INSULATION LOCATION - WHERE TO PUT IT
INSULATION R-Values & Properties
KITCHEN VENTILATION DESIGN
LOG HOME GUIDE
MOISTURE CONTROL in BUILDINGS
MOLD: A COMPLETE GUIDE TO MOLD
NOISE / SOUND DIAGNOSIS & CURE
ODORS & SMELLS DIAGNOSIS & CURE
PLASTER, LOOSE FALL HAZARDS
PLASTER TYPE IDENTIFICATION
PLUMBING DRAIN NOISE DIAGNOSIS
PLUMBING NOISE CHECKLIST
ROOF NOISE TRANSMISSION
ROOF VENTILATION SPECIFICATIONS
SLAB CRACK EVALUATION
SOUND CONTROL in buildings
Splits in Structural Wood Beams
STAIRS, RAILINGS, LANDINGS, RAMPS
SUMP PUMPS GUIDE
THERMAL EXPANSION of HOT WATER
THERMAL EXPANSION of MATERIALS
TRUSS UPLIFT, ROOF
VENTILATION in BUILDINGS
WALL FINISHES INTERIOR
WIND WASHING INSULATION At EAVES
WINDOWS & DOORS
WOOD FLOOR DAMAGE
Building Noise & Sound Control: This article series presents methods and materials used to control sound transmission in buildings: how to make a quiet home, office, or place of business using sound isolation for ceilings, floors, walls, plumbing, etc.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
Our building sound control articles begin here at SOUND CONTROL in buildings. Other noise and sound diagnosis and control articles are found at NOISE / SOUND DIAGNOSIS & CURE where we describe how to locate the source of, identify and correct various building sounds and noises indoors or on occasion, noises from outside that penetrate indoors at annoying levels.
This article series discusses noise and sound control in buildings, and includes excerpts or adaptations from Best Practices Guide to Residential Construction, by Steven Bliss, courtesy of Wiley & Sons. The page top illustration from the above text shows an example of a design to reduce transmission between building floors.
Because of its stiffness, wood framing (photo at left) readily transmits low-frequency sounds and impact noises through wood- frame houses. This is particularly a problem in floors and walls separating two housing units, but it can also be an issue within a single-family home.
For example, a person with a home office or music room might want to isolate it acoustically from the surrounding rooms so meetings or music proceed in private and so outside noises will not intrude.
Bedrooms located under living spaces can also require special treatment to reduce impact noises from above.
Another kind of noise control is important where a house sits by a highway or under a flight path.
The goal here is to keep outdoor noises from entering the house by reducing sound transmission through windows, doors, and exterior walls and ceilings. Special acoustical windows rated for low sound transmission are often required for substantial reductions in outside noise.
Sound can travel through both air (airborne sound) and solid materials (structure-borne sound). Structure-borne sound can be directly imparted to the building structure by a vibration, such as a humming compressor, or by direct impact, such as a boot stepping on a hardwood floor.
As sound energy travels through a building, it changes from one type of transmission to the other and back, losing energy in each transition. Because of its rigidity, wood framing is a very good transmitter of low-frequency sound and hollow wall cavities and thin doors do little to reduce sound transmission.
Sound levels are measured in decibels (dB), which are on a logarithmic scale. A sound increase of just 10 dB indicates an increase of ten times the intensity, although our subjective experience is that the sound is twice as loud.
Decibel levels for common sounds are shown in Table 5-14 at left.
Continuous exposure to sounds above about 85 dB can cause hearing loss in most people.
Sounds in an acoustically “live” room with all hard surfaces will seem loud and harsh due to the sound reverberating off the hard surfaces.
Adding sound-absorptive materials, such as carpeting and soft furniture, will make sound softer and more pleasant within the room, but will do little to reduce the transmission of sound to adjacent rooms.
To reduce transmission requires sound isolation strategies, typically using high- mass materials, double-framed walls, or resilient connections between the drywall and framing.
To keep airborne sound from passing through walls and floors, there are four main strategies:
A cavity with fiberglass is far more effective at blocking sound if the two wall surfaces (or ceiling and floor surfaces) are mechanically decoupled as in a double-stud or staggered-stud wall. Resilient channel works essentially the same way by breaking the vibration path from the stud or ceiling joist to the drywall.
The hardest sounds to block are low frequency, such as the thumping of a stereo bass. Using decoupled construction, such as double walls or resilient channels, is effective.
Where that is impractical, adding mass can also be effective. Very massive, non rigid materials such as lead or sand are ideal, but doubling or tripling the drywall is also helpful.
-- Adapted with permission from Best Practices Guide to Residential Construction.
Additional suggestions for improving the noise transmission resistance of buildings is found in article links listed at Related Topics under SOUND CONTROL in buildings. Be sure to also review Roof & Structure Noise Transmission.
Continue reading about methods for sound control in buildings by using the links provided just below.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the search box below to ask a question or to search the InspectApedia.com website.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.
As stated in Best Practices Guide to Residential Construction: Use fiberglass ductboard or fiberglass duct liners to quiet the noises of fans and moving air. Avoid sharing a common duct between two rooms that need sound privacy.
Elaborating on some duct insulation considerations: HVAC experts advise us that conventional practice is to insulate the interior of metal ductwork in order to minimize transmission of HVAC equipment sounds throughout a building. Some fiberglass duct liners are plastic coated and may be able to be cleaned using gentle procedures. But most common is the use of un-faced fiberglass duct interior insulation, typically treated with a surface resin binder to help reduce movement of fiberglass particles into the air stream.
Our fiberglass lined duct insulation photo (left) shows clean new metal ductwork with a pink fiberglass mat sound and temperature insulation installed on the duct interior.
However our work on indoor environmental and air quality topics suggests that from an indoor air quality maintenance view, we prefer to see insulation on the exterior of metal ducts. That approach permits the ducts to be cleaned, and it reduces the chances of mold growth in the ductwork. See DUCT SYSTEMS and see HIDDEN MOLD in OTHER PLACES for more about places to look for duct system defects and hidden mold on HVAC systems. Mold in Fiberglass Insulation illustrates problem mold growth in fiberglass inculation including in duct systems.
Construction of HVAC ducts from foil-faced insulating board combines sound and temperature insulation with aluminum foil to product ductwork that is quiet and cleanable.
As we show in our photo (left), white noise generators may also be used in locations where an extra measure of privacy is required. This installation is in the waiting room outside offices used by psychotherapists.
White noise is a sound containing a blend of all the audible frequencies distributed equally over the range of the frequency band. When this sound is generated it tends to make unintelligible or even less noticeable other sounds such as nearby conversation.
The proper setting for a white noise generator is not to make the output as loud as possible. Rather, set the volume on the white noise machine to just mask the noise (or conversation) to be overcome. Setting the white noise volume higher than that level risks making the white noise itself an annoyance in the building.
Shown is the Sleep Mate™ sound generator produced by Marpac. In addition to white noise, sound conditioners may produce sounds of nature such as that of a river or brook, lakeshore, surf, thunderstorms, or rainfall. Sound Screen® and SleepMate® are registered trademarks owned by Marpac Corporation.